Replacement of a cast iron pipe Ø 100 mm with diameter upsizing
On behalf of the DUNEA water utility the comapny BAM Nelis de Ruiter in Rijswijk (South Netherlands) BAM has replaced a defective cast iron pipe G Ø 100 mm a PE-HD pipe Ø 160 mm over 532 m length with applying the static pipe bursting method GRUNDOBURST 400G3. To be able to directly pull in the larger diameter PE HD pipe an upsizing head Ø 200 mm was used.
For controlling the max. permissible tensile load of 6,7 t the tensile load measuring device GRUNDOLOG III was mounted to the inside of the new pipe. The measuring results proved that the average value of 5.25 t was not exceeded at any time. Icnluding set up and works the replacement job was done within 3 days.
|Client: ||DUNEA DUin & Water,Netherlands |
|Contractor: ||BAM Nelis de Ruiter, Halfweg, Netherlands |
|Place: ||Rijswijk, Netherlands |
|Date: ||03. - 05.02. 2014 |
|Equipment: ||GRUNDOBURST 400G3 |
|Old pipe: ||Cast iron Ø 100 mm |
|New pipe: ||PE HD TS Ø 160 mm |
|Replacment length: ||532 m |
|Uspizing head: ||Ø 200 mm |
|Special: ||Tensile load measuring with GRUNDOLOG III 40T |